To buy an energy-efficient room air conditioner, you must first determine what capacity, or size, you need. This is important for two reasons:
Use the simple calculation method described below to estimate the cooling capacity you'll need to maintain a temperature of 24°C with a humidity level of between 30 and 50 percent. You can find a more detailed calculation method in another NRCan publication entitled Air Conditioning Your Home (the "Useful Information Sources" page explains how you can order this booklet or view it on-line). If you're cooling a large space, consult a qualified contractor who will consider such factors as the amount of space to be cooled, the number of occupants, the insulation levels and the size, orientation and R-value of windows and doors.
To calculate floor area, multiply the length of each room or open space by its width. Don't estimate - take a few minutes to measure accurately. Units are often bought to cool one or two rooms. Enter your numbers into the blanks provided. (The calculation for a typical open-concept living/dining room will guide you through the process.)
|Length||x||Width||=||Floor Area of Space To Be Cooled|
|20 ft.||x||12 ft.||=||240 sq. ft.|
Remember to combine the total floor area of all the space you'd like to cool with a single air conditioner.
|Total Floor Area||Basic Cooling Capacity|
|65-93||700-1 000||15 000|
|93-111||1 000-1 200||17 700|
|111-149||1 200-1 600||19 000-24 000|
|149-167||1 600-1 800||24 000-27 000|
|167-260||1 800-2 800||27 000-33 000|
* Based on rooms with two occupants and average windows, insulation and sun exposure.
|Total Floor Area to Be Cooled||needs||Basic Cooling Capacity|
|22.6 m2 (240 sq. ft.)||6000 Btu/h|
Note: If cooling capacity is more than 12 000 Btu/h, consider installing two smaller units. Otherwise, a single unit might require a larger amperage circuit (20 to 30 amperes) or a dedicated 240-volt circuit; consult an electrician for more information.
If a question doesn't apply to your situation, leave the space blank. Then add or subtract from the basic cooling capacity to arrive at the approximate size of room air conditioner you should buy.
|Additional Sizing Considerations||Add To Or Subtract From The Basic Cooling Capacity
|If the space faces due north or northeast or is heavily shaded, subtract 10 percent of the basic cooling capacity.||X 0.10 =
|If the space is extremely sunny (e.g. windows face west and southwest), add 10 percent of the basic cooling capacity.||X 0.10 =
|If the space is poorly insulated, add 15 percent of the basic cooling capacity.||X 0.15 =
|If the space includes a working kitchen, increase cooling capacity by 4000 Btu/h.||+ 4000 =
|If more than two people regularly occupy the space, add 600 Btu/h for each additional person.||__ (number of additional people) x 600 =
|If the air conditioner will run only at night, subtract 30 percent of the basic cooling capacity.||X 0.30 =
|Approximate size of room air conditioner to buy.||10 600Btu/h